Most Popular Articles
Tower Light Flasher Failure AlarmThis tower light flasher interface uses a 555 timer as a missing pulse detector. It was adapted from the Missing Pulse Detector The Forrest Mims Engineer's Notebook II by Forrest Mims.
The incoming dc pulse (3) is buffered by Q1, which provides the flash telemetry indication (1) and triggers Q2. When Q2 fails to discharge the C1/R1 circuit, U1 times out and provides a logic low to pin 3, illuminating D2.
|D1, 2, 3||LEDs|
The circuit can be built on a single PC board measuring about 2.5" square.
Diodes D4 and D5 were added by the designer to better interface with his station's MRC remote control. The diode polarity may need to be reversed depending on the relationship between the interface's voltage and the remote control's status voltage.
By changing the value of C1 and R1, the time delay can be adjusted. The current values provide about a 15 second delay until an alarm condition is indicated in the absence of any flash pulses.
The external connections noted are:
P . . . . power
0 . . . . flash failure alarm
1 . . . . flash status output
2 . . . . ground reference for point 3
3 . . . . dc pulse from tower lights
The image below can be used as a template to create the circuit board.
Information provided by John Harris, KUAC-FM, Fairbanks, AK.
Today in Radio History
The history of radio broadcasting extends beyond the work of a few famous inventors.
Read each issue online in our Digital Edition Format in your Web browser.
EAS Information More on EAS
The feed provides feeds for all US states and territories.
Need a calendar for your computer desktop? Use one of ours.
Information from manufacturers and associations about industry news, products, technology and business announcements.
Townsquare Media's WGRD builds a new studio for their syndicated morning show including video
Browse Back Issues[an error occurred while processing this directive]
Also in the September Issue
- Trends in Technology: Electronic News Gathering for Radio
- Tower Rules Update
- AM NRSC Measurements
- Field Report: FLIR ONE
- Small Remote Controls