Most Popular Articles
Something new for news radio
A single 30kVA UPS is used to hold all critical equipment up during any change from utility power to emergency generator power. A 180kW diesel generator available from within the company was used to supply emergency power. This is the first time the station’s emergency system has been independent from utility-provided fuel. Utility power is supplied to the building on two independent feeders adding to the reliability of Utility power.
Integration of the entire system was managed through Radio Systems. The com- pany is local to the area and worked with our extraordi- narily short schedule for integration brought on by delays and complications with construction. Extend- ing the timeframe of the project was not an option because there was a hard exit date from the existing facility with financial penal- ties. Plus, it was set to be demolished.
With the studio furniture being constructed in Phila- delphia, we were able to have it all shipped to Radio Systems to be pre-wired. This allowed integration tasks to occur at a time when the space had not yet been turned over to us. As soon as the studio furniture could be set in place, it was not only quickly installed but studio wiring was nearly complete. In some cases, studio equipment was already mounted in the furniture.
Studio-to-TOC cabling was performed as part of the construction contract. For the most part, the entire facil- ity is wired with CAT-5e multi pair cable. The TOC was released for integration before the rest of the space. Radio Systems worked with a cabling company to speed the installation of the backbone wiring to the TOC. With the use of Studio Hub as the wiring system, the TOC came together relatively quickly with few wir- ing errors. Wiring updates were easily accomplished because in most cases it was only a matter of moving a cable to another RJ-45 connector. Pre-wiring the studios off-site saved both time and money and allowed the facility to be test-ready in less than two weeks from furniture delivery.
Rack layout and documentation was done in advance so chunks of work were delegated and performed almost around the clock. Given the short and diminishing time line, integration occurred around the construction contractor as they finished trim and punch list items.
Move in day
SAS remained on-site after initial programming to insure against operational problems and to cover programming changes for items that may have been missed during the initial configuration, or added as scope changed. The system was tested from microphone to STL and was air- ready. To make the transition seamless, the new facility fed the back-up STL and the handoff could be made via remote control.
When something goes wrong in life, it will often be at the worst possible time. On the night of the switch to the new facility, everyone from the engineering staff, the integrator and SAS representatives were on-site to resolve any problems. Then it happened: The new building experienced a power failure. At least response time was immediate. The incident was very revealing and tested all of our back-up systems. We also discov- ered that some things were on emergency panels that shouldn’t have been and vice versa. With that out of the way, there was a new confidence that everything would be right the next time there is a power failure.
KYW went on the air from the new facilitywith very few problems. Most of the issueswere operational and resolved when everyone became familiar with the studio layout.
Now that it’s finished
There were challenges throughout this project. As I mentioned before, delays related to construction did not give us the time we would have liked for integration and training. Most of the delays were from surprises due to issues that come with a 36-year-old building. These included, but were not limited to ADA compliance, life safety and general changes in the building codes that required updating during construction. Budgets had to be modified due to an unprecedented rise in the cost of construction materials.
Although pre-integrating the furniture off-site saved time and the cost of labor, this created another problem in the area of assembling the furniture when it arrived. Some of the wiring devices and equipment were in the way of key fastening points and this slowed the furniture installation.
The HVAC main and supplemental systems were designed around specifications supplied by the building management. Upon completion of construction, build- ing-delivered air did not meet specified parameters. This meant several office areas were not as cool as they should have been. Rebalancing of the system has resolved most of those issues.
After the dust had settled and the moving boxes had been emptied, everyone was proud to be a part of the new facility. There is an intangible benefit to the entire operation when employees feel good about the environ- ment they work in. The new studios for KYW met all of the design goals we set at the beginning of the project and the result is a facility that will be easy to use and manage into the future.
Steinnagel is the Mid-Atlantic director of engineering/mid-Atlantic for CBS Radio.
Facility photos courtesy of Bloomfield and Associates, except TOC, which is courtesy of KYW.
KYW Equipment List
- Air Tools 6100
- Belar LP-1a AM
- CBT Classic On-Air Light
- Circuitwerkes AC-1, AC-12
- Crown D-75
- Digidesign Mbox 2
- Digigram VX222 v2
- Electro-Voice 309A, RE-16, RE-20
- Enberg BA12CTL, BA12WL, FN3
- ESE LA12F, ES-185U/NTP, ESE HR TOH
- Eventide Eclipse
- Fostex 6301B, RM-1
- Harris Intraplex HD Plus
- Henry Engineering Matchbox
- HHB CDR-830 Plus
- JBL 4408
- JK Audio Quick-tap
- Microwave Filter FD6367
- Middle Atlantic Drift, Gang-10 Kit, Mag-1/2, MRK-4031, MRK-4036, MV-RR40, MW-VT, PD-1220J-IG, RSH4A3S, SPN-40-312, SPN-40-36
- O.C. White long and short booms, risers
- Omnimount 30.0 CA-PA, MT600
- Radio Systems DI-2000, integration services, Studio Hub+
- Rainwise MKIII
- Rane HC6
- SAS Rubicon SL
- Sony 7506
- Soundcraft EPM-6
- Studio Technology furniture
- Symetrix 528E
- Tascam MD-350
- TOA A906 Mark II
- Yamaha SPX-2000
Acceptable Use Policy blog comments powered by Disqus
[an error occurred while processing this directive]
Today in Radio History
The history of radio broadcasting extends beyond the work of a few famous inventors.
EAS Information More on EAS
The feed provides feeds for all US states and territories.
Need a calendar for your computer desktop? Use one of ours.
Information from manufacturers and associations about industry news, products, technology and business announcements.
Townsquare Media's WGRD builds a new studio for their syndicated morning show including video
Browse Back Issues[an error occurred while processing this directive]
Also in the September Issue
- Trends in Technology: Electronic News Gathering for Radio
- Tower Rules Update
- AM NRSC Measurements
- Field Report: FLIR ONE
- Small Remote Controls