Sierra H: The Transmitter Goes Over the Mountain
The Flexiva itself offers several additional monitoring options, including front panel visuals and an IP connection with a richer graphical representation. We also interface with Burk ArcPlus remote controls so I can call in by telephone when necessary. An SNMP interface opens up an entirely different monitoring universe that we have just started to explore.
The transmitters have been stable, with just one glitch related to an air conditioning problem -- and the main reason we're adding the third AC unit this spring. The APC setting had inadvertently been turned off in one of the transmitters, and when an AC unit locked up the transmitter didn't fold back power to compensate.
Eventually, a piece of transmission line failed, with minor damage to the directional coupler and controller board. The backup was put immediately into service and repairs to the main were quick and easy to perform.
An emerging benefit of the transmitter installation correlates with the monthly operating costs. We initially couldn't tell much difference between the Flexivas and the Nautel, but with two transmitters running for several months everyone is quite pleased with the electrical draw. They don't jump around or spike and keep very consistent output power. This results in stable draw, which results in predictable monthly bills. The lack of fluctuations in power is especially helpful for the in-line surge suppressors. Additionally we have not experienced a single power supply or PA module failure to date.
As of press time we have made it through the rainy autumn season, which brings an assortment of storm-related electrical activity. With winter passing in the rearview mirror, it's time to look forward to getting our HD Link on the air -- and hopefully dodging any repeat forest fires this spring and summer.
Belkin monitor rackmount w/built in KVM
Bird BPME display panel, power sample section
Broadcast Tools DMS-III, Silence Sentinel Basic
Burk ArcPlus, Plus-X AC-8, Plus-X ICRU, Plus-X IIU
Cummins 800A, Cummins/Onan propane genset
Dielectric 3-1/8" four-port motorized coaxial switch, dual switch controller
ERI six-cavity T combiner
Harris Flexiva, Intraplex STL HD T1
Henry Engineering Powerswitch
LEA DS30S, Powervantage surge suppressor
Liebert GXT2 UPS
Middle Atlantic PD-815
Myat, Shivley, Dielectric 3-1/8" rigid line and components
Orban 6300, 8600FM
White is president of Klein White Broadcast Engineering. He can be reached at email@example.com.
Acceptable Use Policy blog comments powered by Disqus
[an error occurred while processing this directive]
Today in Radio History
The history of radio broadcasting extends beyond the work of a few famous inventors.
Read each issue online in our Digital Edition Format in your Web browser.
EAS Information More on EAS
The feed provides feeds for all US states and territories.
Need a calendar for your computer desktop? Use one of ours.
Information from manufacturers and associations about industry news, products, technology and business announcements.
Staying on-air is priority #1, but 100 percent redundancy comes at a cost.
Browse Back Issues[an error occurred while processing this directive]
Also in the November Issue
- Music is Everywhere at WTMD
- FCC Looks to Update RF Exposure Rules
- Government Shutdown Causes FCC Delays
- Applied Technology: Wheatstone baseband192
- Side by Side: Video Cameras
- Exploring More from Google Earth
- The History of W9BSP